This high quality 2 litre wet chemical fire extinguisher is supplied with a securely strapped wall bracket, a fire extinguisher location sign, and a wet chemical fire extinguisher identification sign.
When to use:-
Class A fires – Ordinary combustibles
Class F fires – Cooking oils and fats
Where to use:-
This wet chemical fire extinguisher is used for fighting deep fat fryer fires in a restaurant or commercial kitchen environment. The 2 litre wet chemical fire extinguisher will protect up to 25 litres of cooking oil. Above that quantity please use the 7 litre wet chemical fire extinguisher. This fire extinguisher works by quickly applying a layer of wet chemical on top of the fire therefore removing the oxygen and preventing re-ignition. The heat source must be removed, by simply turning off the power source, if safe to do so.
This fire extinguisher can also be used for class A fires for ordinary combustible materials such as paper, cardboard and wood in place of a plain air / water fire extinguisher.
Where not to use:-
This wet chemical fire extinguisher is NOT TO BE USED for electrical fires under any circumstances.
For a guide to selecting the correct portable fire extinguisher for specific classes of fires please refer to the FPA's Portable Fire Extinguisher Guide which can be viewed and purchased from us here
||Wet chemical powder fire extinguisher
|Size (Net Mass)
||up to 25L capacity Deep Fat Fryer
||1350kpa (13.5bar / 363psi) at 23 Deg C
|Periodic Test Pressure
||2.5mpa (25bar / 363psi) every 5 years
||Stainless Steel Body / Stainless Steel Handle / Brass Valve Body
||Certified and approved to AS/NZS 1841.3 (2007)
||Red with an oatmeal band or label
* Various factors affect coverage such as hazard risk, travel distance to fire extinguisher and rating of fire extinguisher. See AS2444:2001 for more details.
When you buy this fire extinguisher, you receive the following items included in the price:-
- Maintenance tag -punched with the month and year that it left our premisesin accordance with AS2444. Identifies when the next 6 month inspection is due.
- Maintenance tag ring
- Fire extinguisher location sign (requirement of AS2444:2001) - SGEL
- Wet chemical fire extinguisher identification sign - SGWETC
- Secure wall bracket (Powder coated steel frame / Stainless band & fastener)
Wet Chemical Type Fire Extinguisher MSDS Document
While every effort is made to ensure the specifications and pictures are correct, we source products from a number of manufacturers, which leads to differences both visually and physically between equivalent products. If you need current up to date specifications, please Contact Us